Log in to follow, share, and participate in this community. Is it not in line with NFPA 72 to have the horn/strobes in the AOR, silenced due to not being able to hear the voice-intercom in that area or maybe using a different tone/sound, like a chime only in the AOR? I've been looking in NFPA 1, 101 and 5000 for a reference to retractable belt barriers (such as Tensabarriers TM), but I have not found any. Specifically I am wondering if there is a clear statement discouraging user... Most commercial gas range manufacturers state that their product is for use on a non-combustible floor. If a restaurant is planned to be installed in a building with an existing wood-framed f... Has anyone used a door gap gauge from www.allthingsinspector.com ? This document is a paper I wrote a few years ago. The idea of patient safety, proper egress is a joke! Monday, February 22, 2010 James Hamil Allen Hancock College FT 104 Building Construction/ Fire Protection S... We are under the jurisdiction of CMS and other regulators. We are a Skilled Nursing facility in northern California. It is my belief that we need to be following NFPA 101 2012 is this correct? Would there be other jur... NFPA 96-2017 - 10.4.1 requires the gas and electrical to be shut off for heat producing equipment under an exhaust hood upon the activation of the fire-extinguishing suppression system. For gas fired c... Code states egress from a room or space shall not pass through adjoining or intervening rooms or areas, except where such adjoining rooms or areas and the area served are accessory to one or the other, are not a ... You know there needs to be a cheat sheet for when notification is needed on a project! 9.6.3 Occupant Notification. 184.108.40.206 Occupant notification shall be provided to alert occupants of a fire or other emergency wher... How can I design an effective PA system zoning? Firstly, I am in Puerto Rico. I've searched the Codes but can't find an applicable one for this situation. We have a restaurant and want to have a gas operated outdoor grill. It will be sitting in an outdoor, open air... Hi All, Is it possible to help guide me to find out some information about installing wood panels which are Class A fire rated? My question specifically related to the gap of air behind a panel once installed. ... Will 606.2.1 allow you to shut down an hvac unit with an open air return under 15001 cfm with area smoke detectors in the room of the hvac unit? Note that the return air is coming from holes in the walls pulling from ... Hello all, i have an inquire regarding emergency preparedness & response in case of incidents and fire, one of our client which is a logistic company based in a sea port asked me to held for them a training to tra... Dear Team I am going to do corridor smoke test in one of residential building; I need to know the following: a) What is the amount of smoke needed by smoke machine and what is the time required such process? ... while designing canopy for exterior canopy car shade of steel and fabris as a shade, its required in NFPA 101 and 701 to pass 1 of two tests, Its already passed test number 2. How do we know how many hours... Does anyone have a fire safety inspection form they would like to share Dry riser system to be given in basements of a mixed occupancy of a mall. The mall is having 10 basement parking level. As per NFPA, how it could be considered to design. Is there any code to have a Dry riser / pre ... Many countries (Canada, Australia, nearly entire Europe, Japan) use the pictogram with the green running man as an exit sign, meanwhile the US uses a green or red "EXIT" sign. My question would be whether it is allowe... 2015 NFPA 101:220.127.116.11 What is the required minimum clear egress width for the back-bar employee area in a restaurant bar (new construction)?