Log in to follow, share, and participate in this community. We need to install a Kidde wet chemical system in our kitchen. Unfortunately, the supplier who provided the necessary support is no longer in the market. We are totally new to the system. It's a small system with one ... we have a diesel and electric pump operating in auto mode. As per NFPA 20, the pressure setting for the pump shall be churn pressure+ static pressure. while doing the actual performance test, the churn pressure( zer... Hello. The question I have is where in NFPA does it say that if you exceed a certain ceiling height you are to use type "xyz" sprinkler heads. Storage height is minimal, 12' at the most. lets just say for talking purp... Why not consider a dry means of fire control? I have one using pure, cohesive Nitrogen gas cloud technology. The Fixed Nitrogen fire control systems store liquid Nitrogen above the system which need refilling m... Hi, i need expert opinion on subject mentioned, I m working in MEP contracting company as a mechanical engineer, I need to perform fire sprinkler hydraulic calculation for one of our pr... Hello, how do drivers for fire pumps in NFPA 20 sprinkler installations have to be sized correctly? Do the drivers have to be sized only up to the 150% of the rated flow or do the drivers have to be sized to the non-o... Dear Sirs, in my understanding of NFPA 72, Chapter 24, the Fire Alarm Control Panel can monitor and control the fire suppression system applied to specific areas at the same time that other rooms of the building, for ... Hi, my name is Diego Sandoval and I am designing and FIRE FIGHTING SYSTEM. I have a question related to NFPA 20. I want to know if I can return the relieves towards suction lines in FIRE PUMPS WITH DIESEL ENGIN... Hi, I have been working for design of fire sprinkler system for ICE cream factory. It consist of (1) Installation at packing hall where the temperature of packing hall is 15degC. (2) Installation at Cold Stora... We have a gravity fed water supply located on a mountain that supplies the city's water system. This supply is being recommended as the water supply for a project at a lower elevation. The water supply is being booste... In NFPA 25 , regarding Fire water pump Annual Performance test, one of the acceptance criteria is specified as pump performance shall be within 95% of the initial unadjusted field test curve. If the initial fiel... The July 2020 edition of Professional Safety Journal (page 10) discusses a current study by Mauge-Lewis and researchers regarding growing concerns over possible adverse health effects of AFFF (Aqueous Film-Forming Foa... You do not have access to this content's place Hello, i have a question about dry fire extinguish system. Can i use dry chemical extinguish sprinklers on the car parking? NFPA 13 (2020 edition) and earlier editions was silent in putting a limiting velocity in the piping along cross mains and branchlines of its sprinkler system. There are some individuals who specify that the maximum ve... Reference: NFPA 13 (2019 Edition) 126.96.36.199 Friction Loss 188.8.131.52.1 Pipe friction loss shall be calculated in accordance with the Hazen–Williams formula with C values from Table 184.108.40.206.1, as follows: (9) Fr... I think to use a circuit breaker with only magnetic protection for a single fire pump (without a jockey pump).Should the FRAME of the circuit breaker meet the rated current OR just the current sensor of the circu... FIRE GUARD See link on a new device by Fire Guard that claims a fire suppression agent (6-inch ball) can extinguish a fire in an area up to 905 square feet. Any information the NFPA has on this type of e... NFPA 20 (2019 edition) Section 220.127.116.11 discusses on the jockey pump sizing to replenish the pressure due to the allowable leakage and normal pressure drops, with a suggestion (a guideline) to select a jockey pump tha... cuando tengo un edificio clasificado como de no gran altura puedo colocar sistema de tubería vertical clase 1 (manual húmedo), sin tanque ni equipos de bombeo, solo que dependa del departamento de bomberos.