Hey all, I'm trying to figure out where in NFPA 72 could I find Fire Detection for a Diesel Generator. In Laser Tag Arenas, there are team Bases. Each project has different themes and therefore have different designs for Bases. Most Bases have an overhead element connected to 2-4 walls. Question: What specific ... Does this building require a suppression system? Conditions: Existing motel built in the late 1960s Abandoned (4-6 years) Unde... In a building where above ceiling there are vehicles circulating, which creates vibration underneath, and there is a building expansion joint, due changing from this ceiling to another stationary structure, is it... In the NFPA2001 standard, the definition for shall says it is a mandatory requirement. As far as I know, something is only mandatory if stated in Legislation, Regulations or Official Acts? Does this mean the part... Is it required for an Ansul System to report to the fire panel? Hi, I would like to know which standard in NFPA specifies the selection of Fire protection method for pharmaceutical plant included clean rooms with A to C class. Can anyone specify which standard in NFPA specifi... Dear Sir I have a diesel tank located at the basement in a dedicated room with 3 hours fire rated enclosure with capacity more than 5000L . What is the best fire protection system for such application. Is auto... Hi, I would like to know which standard in NFPA specifies the selection of Fire protection method for pharmaceutical plant included clean rooms with A to C class. Can anyone specify which standard in NFPA specifi... NFPA 13 184.108.40.206 says sprigs 4 ft and over shall be restrained againist lateral movement. Does any one know what type of restraint is to be used. Can CO2 Systems still be used. Have a building with a co2 system that needs some work can the system remain or does it have to be removed. All Retail Shops are recommended to be provided with Quick Response Sprinklers. Fire Size used in the calculations is 2.5 MW considering Quick Response Sprinklers in compliance with BS 7346 Part 4 Table 3. ... Is there any reference in NFPA 96 that would prohibit a company from installing a vinyl wrapping on their commercial hood system? I am told that the wrap is self-extinguishing. Or is this one of those times where a cu... Just few days ago had a training about https://catalog.nfpa.org/NFPA-72-National-Fire-Alarm-and-Signaling-Code-2019-3-day-Classroom-Training-with-Certificate-of-Educational-Achievement-P458.aspx NFPA 72 (2019) Classro... According to NFPA 13 (2013) 7-10.3.3 sprinklers or spay nozzles have to be no more than 5'-0 from the duct entrance. per the table A.7.10.2 it shows (D) being measured from the inside of the duct. Would this still be ... Is it ok to use pendant sprinkles in an open ceiling configuration if the distance from the sprinkler deflector and the ceiling are within 12 in. I have been told that only upright sprinklers are allowed in... WE ARE HAVING HELPAD AREA IS 40 x 40m and landing area is 20x 20m. Helipad is more than 40m away from buildings. As per NFPA 418 do we need to have foam system with deluge. What are the conditions to avoid foa... We have a free-standing raised Helipad being built adjacent to an existing Hospital. There is to be an enclosed Bridge/Link that connects the Helipad to the second floor of the hospital to transport patients from... Hello there, i have a fire alarm project we have installed 20 addressable FACP, but the consultant asked us to connect all panels together so far if there is an alarm in panel number 1 it will also appear in the other... new code states that fusible links shall be within 12" of the ceiling. Would existing installations be grandfathered in, or do I actually need to move them all?