I really want to know for a new study. PLZ TECHNICAL QUERY: #FIRE HYDRANT For a project site where Fire Station is within travel distance of less than 60 seconds, do we need a private hydrant system OR can we avoid hydrant system as CIVIL DEFENSE FIRE ... The Fire Protection Person of the Year Award was created in 1973 to recognize significant achievement in the protection of humanity and the environment from the ravages of unwanted fire and an outstanding contribution... NEC 2014 Section 250.52(A)(3) states that 1/2 inch or larger rebar bonded by tie wire (20 ft or more) can be used as the grounding electrode. When attaching the grounding electrode conductor to the rebar to be encased... The Advantages of firesafetycloud.com in Fire Safety Management. The consequences of poor fire safety practices and a lack of emergency planning can pose a serious threat, not only to the building and... For many, fire sprinklers are like ocean buoys: people know of them, and that they do something important. But that is often where consideration stops, and the same can be said for home fire sprinklers. ... Is it possible to install foam chamber in geodesic dome tank roof (witn internal floating roof) instead of foam chamber in shell tank?? I have not found something about in NFPA 11. What criteria I should take i... Hi, i would like to know article 220-22 still available in NEC? as we can't find in our book. Thanks hi everyone, I am new to the field and i need your advice. i couldn't find a rule of addressable fire system in NFPA 72, where does require to install "addressable fire system" and "conventional fire system... Dear All A question to members of this forum. NFPA describes "Listed" as Equipment included in a list published by an organization that is acceptable to the AHJ. OHSA (under United States department o... In Chapter 5 in NFPA 2001, edition 2018 There is a table, Table 220.127.116.11 Atmospheric Correction Factors. ¿What would be my correction factor if my equivalent altitude is over 14,000 ft? ... Hello all. I have an easement on my property that runs from an electrical pole on the road, back, underground about 800 feet to a neighbors yard where it stops at a transformer. There is a creek the runs perpe... Hi What is the standard size and length of Fire Hose Reel or Class II Hose Reel System? Where exactly is this mentioned in NFPA standard? As per my knowledge Fire Hose Reel standard is 25mm dia and 30mtr ... We have a gravity fed water supply located on a mountain that supplies the city's water system. This supply is being recommended as the water supply for a project at a lower elevation. The water supply is being booste... With regard to emergency evacuation drills in schools, has anyone come up with modifications (or have suggestions) due to COVID as we approach the new school year? Physical distancing will be the challenge as al... The ripple effects of the record-breaking property losses in California due to wildfires in 2017 and 2018 are still being felt as survivors work to rebuild their homes, local governments scramble to help recover neede... I would like to know if, in a NFPA standard, a formula exist about calculing the initial attack force, for exemple for an industral plant. We know fro residential fire, 10 FF is recommanded, but is there a way to calc... The NFPA Standards Council will be meeting on August 10-13, 2020 by video conference (daily sessions from 10 a.m. – 2:00 p.m. EST until conclusion of meeting). At this meeting, some of the topics the Coun... If the room protected by a fire suppression system has a beam pocket, it is required/mandatory to provide Z1 & Z2 detector in any case? If the room protected by a fire suppression system has a beam pocket, it is required/mandatory to provide Z1 & Z2 detector in any case?