Is it okay to install horizontal split case on "Lift Suction Application" instead of fire pump vertical turbine? is the NFPA allowed this kind of set-up?
the matter between vertical and horizontal just for enough space in that location.
Split case fire pumps are not allowed for lift suctions application. See NFPA 20 section 6.1.2 and section 7.1.1.
Retrieving data ...