Hi everyone, another question here. I already know under CFC Table 1104.18, the maximum common path limit is 100 ft for any S type building. However, I have already heard it twice from other FPEs that it is 150 ft. I even spoke with a high pile storage company that installs racks, that said 150' is permissible. My
Say for example, you have a 120/240 V, 2 pole, 20 A breaker. Does the NEC allow this breaker to serve 2 separate 120 V circuits?