Do I just monitor the sprinkles system????
Helps giving an edition reference also.
Why I hate 101, because you have to jump all over the place.
Appears per 101 nothing is required??
Are you only under 101, or some other building or fire code?
NFPA 1 & 101 this is Florida Fire Code
Will have to look at 1 later, to see what it says
Well NFPA 1 is not much better
I am thinking somewhere it must say you have to at least monitor the system. But does not appear in 300 or less you need a full blown system
18.104.22.168.1* Supervisory Signals. 22.214.171.124.1.1 Where supervised automatic sprinkler systems are required by another section of this Code, supervisory attachments shall be installed and monitored for integrity in accordance with NFPA 72, National Fire Alarm and Signaling Code, and a distinctive supervisory signal shall be provided to indicate a condition that would impair the satisfactory operation of the sprinkler system. [101: 126.96.36.199.1] 188.8.131.52.1.2 Supervisory signals shall sound and shall be displayed either at a location within the protected building that is constantly attended by qualified personnel or at an approved, remotely located receiving facility. [101: 184.108.40.206.2]
220.127.116.11.2 Alarm Signal Transmission. 18.104.22.168.2.1 Where supervision of automatic sprinkler systems is required by another section of this Code, waterflow alarms shall be transmitted to an approved, proprietary alarm-receiving facility, a remote station, a central station, or the fire department. [101: 22.214.171.124.1] 126.96.36.199.2.2 The connection described in 188.8.131.52.2.1 shall be in accordance with 184.108.40.206. [101: 220.127.116.11.2]
Your AHJ (Fire Prevention Bureau ) should be able to help you with your question. You should also inquire about any local code that will affect you question. Please remember that NFPA is mimimal code/standard requirements. Local code/standards come first.
Retrieving data ...