I have a 100 amp breaker feeding a 60 amp sub panel on a rooftop. Would that sub panel need a main breaker or a disconnect?
Anybody respond on here? I told the people installing that it needs a disconect. I'm I right? Figure anything on the roof has to have a disconect within 25'
Code violation; Where is the overcurrent protection for the 60 ampere panel bus rating? The feeder needs to be protected not greater than the panel bus rating or the feeder conductors which ever has the lower ampere rating.
Retrieving data ...