do to low water pressure coming into our building our trip test are not at less than a minute and thinking of splitting system in two. we have a dry and wet system
For a dry system over 500 gallons and up to 750 gallons with a quick opening device, then no time requirement is to be met.
Make sure nothing else drives the 60 second requirement,
Like some of the Tyco attic heads.
Retrieving data ...