Quick question: What is everyone's definition understanding of a "looped water main"?
This is my municipality's requirement: All water distribution systems shall have two connection points or be looped to avoid dead ends. If a looped system cannot be provided, dead end mains shall not exceed 150 feet in length and a fire hydrant shall be installed at the watermain termination point.
Thank you Mr. Norton
Retrieving data ...