Log in to create and rate content, and to follow, bookmark, and share content with other members.
NFPA 15, section 5.3.4, states that copper tubing is permitted in water-filled water spray system. The inference is therefore, that copper is not permitted in dry systems, which is a typical deluge system. Can anyone clarify this assumption is correct a
Working on a project where the client is insisting we use copper (90/10 copper-nickel) pipe for the water-spray systems. Need to clarify why NFPA 15, 5.3.4, only mentions the use of copper in water-filled water-spray systems (ours is dry).