Two separate systems, now in the same building after a wall was removed, "cross-trigger" each other. Two locators, two FACP's, two separate indication circuits. Is this allowed? If so, what is the code reference in NFPA72 2010
I do not think it is addressed in 72
As long as each trips the other, that is good
Maybe see if one panel can handle the entire load?
Or plan to replace both with one
NFPA 72 2016 Section 23.8.2
Thanks for the section reference !!!!
Retrieving data ...