Need to respond to a Fire comment and do not have the Code at hand. Thanks.
You can access the standards for free, just sign up:::
You do not say which year edition
16.4.2 Temporary Separation Walls.
Protection shall be provided to separate an occupied portion of the structure from a portion of the structure undergoing alteration, construction, or demolition operations when such operations are considered as having a higher level of hazard than the occupied portion of the building. [241:18.104.22.168]
Walls shall have at least a 1-hour fire resistance rating. [241:22.214.171.124]
Opening protectives shall have at least a 45-minute fire protection rating. [241:126.96.36.199]
Nonrated walls and opening protectives shall be permitted when an approved automatic sprinkler system is installed. [241:188.8.131.52]
Retrieving data ...