Looking to get an ultrasonic flometer in order to perform annual flow test on fire pumps.
That is a new one, have not heard of them used with fire pumps before.
Where would you place the device???
Ultrasonic flowmeter can be used to perform the test but the device is so sensitive to vibrations, and the settings should be done very carefully, othervise the readings may not be acceptable. Installation of the probes should be in line with the instructions of the device provider, and also calibration certificate of the device should have an acceptable range.
Retrieving data ...