Hi, can someone help me figure our the fire rate required for fire hose cabinets?
I can not find it anywhere
If you are talking Class II::
For Class II systems, the minimum flow rate for the hydraulically most remote hose connection shall be 100 gpm (379 L/min).
Max 100 psi, and I think minimum 65 psi
But what is the fire rate requires for the cabinate door? Its in a mall
You want to know if the door has to be fire rated?? as in 1,2 hour rating??
I would say none.
Now if the cabinet itself is in a rated wall, the cabinet itself may have to carry a rating, like an electrical box.
If the cabinet is out in the main mall area, my guess is not rating.
Mostly they happen to be in fire rated walls.. but do you know in which nfpa i can find this .. or its just your guess? Thanks alot
Not a NFPA 101 person, but should be in 101, the chapter 8 that covers rated walls, and that they have to be built and maintained
Retrieving data ...