In NFPA 70 it is indicated that the automatic protection of the drive system with electric pump
must be equal to 6 times the nominal current, however the wires are available for 1.25 times the
norminal current. Accordingly, the wires can be burned without activating the automatic.
I will appreciate my opinion on this point,