hey all i'm new to here . in this occasion i'm need to clarify two doubts. I'm using an IG 100 inert system in my project. its a substation my questions are given below
* Where do i keep the abort switch for the fire suppression abort. now i'm keeping it near to fire suppression panel. Is there's any NFPA regulation for location of abort station
* The ceiling of my building is made as a rib cage structure is there's any special NFPA protocols for spacing of the detectors
i'm attaching the Details with this
i'm waiting for your valuable feedback asap.
thanks all have a good day