I am wondering how many of the fire inspector will be enforcing strictly the requirements per 2012 IFC Table 3206.2 especially section 3206.6 Building access. One fire door per 100 linear feet of exterior wall of the Building is required. Thanks.
I have been enforcing it for 30 years now
Why the question?
Most of the time the required exits, meet most of the requirement.
It is only required along the walls that have high pile stock
This is not an NFPA response as someone might point out.
Retrieving data ...