NFPA 2001 Clarification.
We are under an inert gas system design (IG-541) . Our system is class C fire and according to NFPA-2001 table A.184.108.40.206.b minimun design concentration of 38.5% shall be used.
My concern is related to concetration target to calculate the discharge time. There are two paragraphs on NFPA-2001 that will divert to a different results
220.127.116.11.2* For inert gas agents, the discharge time required to achieve 95 percent of the minimum design concentration for flame extinguishment shall 120 seconds for Class A surface fire hazards or Class C hazards,
According to my understanding and values given at A18.104.22.168.B, time should be calculated to achieve 36.5 %(95% of 38.5)
22.214.171.124.3* The discharge time period is defined as the time required to discharge from the nozzles 95 percent of the agent mass [at 70°F (21°C)] necessary to achieve the minimum design concentration based on a 20 percent safety factor for flame extinguishment.
According to my understanding, to meet this requirement time should be calculated to achieve 32.5 % (95% of 34.2 Class A fire)
I would need a clarification in order to Know which one is the correct result.