NFPA 13 184.108.40.206 states : Hangers shall be designed to support five times the weight of the water-filled pipe plus
250 lb (115 kg) at each point of piping support.
Spec sheets from the pipe ring manifacturer indicates the maximum load for their product. For instance, ANVIL fig 69 pipe ring is rated at 300 lbs for a 1 in pipe ring. The spec sheet clearly states : ''Tapped Per NFPA Standards''
I will calculate spacing for a 1 in schedule 40 pipe (water-filled weight is 2.05 lbs/ft)
Pipe ring max load = (5 x water-filled weight x spacing) +250 lbs
300 lbs = (5 x 2.05 x spacing) + 250 lbs
Resulting spacing is 4.88 ft.
It seems crazy to ask for pipe support every 4ft10in, especially since NFPA 13 table 220.127.116.11 says maximum distance between hangers is 12 ft for 1 in pipe.
It would be much appreciated if someone could tell me what is it I dont get!