What is the distance the hood needs to extend beyond the appliances for a fire suppression system? And where is this noted in NFPA 96?
Some listed the extension is not required, non listed normally six inches.
Will have to look for a reference
ok maybe it is not specified from 2014 edition
5.2 Hood Size.
Hoods shall be sized and configured to provide for the capture and removal of grease-laden vapors
I am use to IMC
This is 2006 edition, does not have the exception for listed hoods:: might be in later edtion
Retrieving data ...