We are installing an Emergency Responder Radio Coverage system in our hotel facility. A 1-hr rated enclosure has been specified to house the equipment. Basically a 6' x 6' room constructed from metal studs and drywall with a rated door and hollow metal frame. The only equipment in the enclosure is the ERRC equipment. No other materials are in the room. The enclosure is within a fully sprinklered space. The enclosure has a smoke detector interfaced to the main fire alarm panel for the facility. 7-story bldg. Occupancy class Mixed R1/A3/B. Construction type 2001 CBC Type II FR. Sprinkler system NFPA 13.
QUESTION IS, DOES THE ENCLOSURE ALSO REQUIRE A SPRINKLER HEAD?