I have a high bay warehouse with an ESFR suppression system. A few feet under the suppression system, there is a run of conduit approximately 4' wide. I have been informed by FMGlobal I need to run sprinklers below the obstruction and meet a 4'x5' cover. This seems a bit excessive and I can not find the requirements in NFPA. Any guidance would be appreciated.