Is the fire pump test manifold mandatory to install where one has an in-line flow meter (venturi) installed, a pitot meter installed and an ultrasonic flow meter available?
Have to check, I want to say yes required regardless
I read required
from the latest 20
A.126.96.36.199 Where a flow test meter is installed, an alternate means of testing, such as hydrants, hose valves, test header(s), and so forth is needed
THANKS FOR THE HELP. Much obliged
GANB Inspectores de Riesgos Asociados C.A.
Telephone: 0212-2426947 / 0414-1976755
Enviado el: jueves, 15 de febrero de 2018 03:29 p.m.
Para: federico pacheco <email@example.com>
Asunto: Re: - Re: Fire pump test manifold
<https://community.nfpa.org/?et=watches.email.thread> NFPA Xchange
Re: Fire pump test manifold
reply from cda cda <https://community.nfpa.org/people/cdafd?et=watches.email.thread> in Fire Protection Systems - View the full discussion <https://community.nfpa.org/message/51356?commentID=51356&et=watches.email.thread#comment-51356>
one year out of three must by water flow the other two its allowed to use the bypass flow meter. NFPA 25
Thnks for the help. I was looking into the wrong standard.
Enviado el: jueves, 15 de febrero de 2018 04:45 p.m.
reply from Steve Cox <https://community.nfpa.org/people/steve.cox2?et=watches.email.thread> in Fire Protection Systems - View the full discussion <https://community.nfpa.org/message/51349?commentID=51349&et=watches.email.thread#comment-51349>
Retrieving data ...