The clean agent units are in cpu rooms and ABC extinguishers are in the access hallways.
I want to say no
Excerpts from the 2018 NFPA 10:
These are the minimum. It would be a good idea to place a sign to use special agent extinguisher on the cpu equipment only. Use the ABC fire extinguisher in the hall for all other fires.
Let me know if this helps.
Thank you for your input! The extinguishers are factory labelled (one can only hope that they are correctly labelled;) I cannot find any requirements for signs specific to the extinguisher agent or intended use - just looking to see if anyone was aware of any.
Retrieving data ...