Hello. What are the design parameters for protection in the NFPA13 for a plastic A double row-rack storage with slatted shelves, storage height of up to 6.1 m and a ceiling height of 15.2 m?
You should apply the parameters found on section 17.2 of NFPA 13. Depending on water availability and budget you can choose CMDA, CMSA or ESFR design parameters.
By the way, the ceiling height is above the currently maximum height of 14.6 m that storage sprinklers can effectively work. A false ceiling will have to be installed in order to protect the storage.
Retrieving data ...