Is there anything mentioned in NFPA about at what height fire hose cabinet to be installed.
Yes. 2016 NFPA 14, Standard for the Installation of Standpipe and Hose Systems has the requirements in Section 22.214.171.124. Hose connections and hose stations must be unobstructed and must be located not less than 3 ft (.9 m) or more than 5 ft (1.5 m) above the floor.
Let me know if this helps or confounds you.
I guess it´s the same for a foam station, I have to check the standard
Retrieving data ...