Is there anything mentioned in NFPA about at what height fire hose cabinet to be installed.
Yes. 2016 NFPA 14, Standard for the Installation of Standpipe and Hose Systems has the requirements in Section 188.8.131.52. Hose connections and hose stations must be unobstructed and must be located not less than 3 ft (.9 m) or more than 5 ft (1.5 m) above the floor.
Let me know if this helps or confounds you.
Retrieving data ...