NFPA 72 - Ch 17:
At one of our buildings, we have magnetic door hold opens for a fire-rated wall opening right next to a cooking hood that has 3 times now tripped a smoke detector….(this wall is not a smoke partition) and the magnetic hold opens release upon smoke activation…..they also initiate a fire alarm. Are they required to be an initiating device? Can they be supervisory?
Thank you! Sam