Could someone explain the basis for arriving 65% of rated head requirement @ 150% of rated flow as per NFPA 20, para 6.2.1
Thanks for your response and sharing tutorial.
Actually I would like to know why 65% is required, for example why not 60 % or 50%.
This should help explain the engineering behind your question.
NFPA20 basic questions
Retrieving data ...