Hello again. Can a quick response sprinkler and a standard response sprinkler be combined in same system?
Standard response sprinklers can be in the same system with quick response sprinklers as long as they are in separate rooms/enclosures. If mixed in the same room, then "skipping" can occur an not control the fire effectively.
I agree with Emmanuel. However, some of the local codes and the occupancy chapters in NFPA 101, Life Safety Code only allow quick response sprinklers. You will need check the building and life safety codes before installing a mix of sprinklers in your system.
NFPA 13 2016
Appears as Emmaunel said
OHHH I am not an engineer, so you can discount my reply if you want
Thanks for the section.
Retrieving data ...