- CFR 1910.333 says "Live parts... shall be de-energized before the employee works on them..."
Does removing the main-service-panel cover (120v) and taking pictures fall under the definition of "works on them"?
-- If so, can the Main Breaker be shut off, or does the service need to be completely shut down behind the panel (at the meter), in order to remove the panel cover?
* This is for inspecting the panel for a potential solar project
***Please reference code/documentation that can be used to support any answers.
THANK YOU for your help !!!