I've been asked to review a schematic which uses a 4/c UF cable to supply (2) 208V 30A branch circuits to a control cabinet. Neither of the circuits requires a neutral.
The circuits originate in the same panel board and the cable contains a single EGC. The cable is Protected by way of EMT for a distance of 25'.
Any help/ code reference would be appreciated.