A Fire hose cabinet is provided at the flat roof of Dubai airport support building in accordance with the NFPA 14-2016, chapter 7, section 7.3.2. Building is 2-storey and 8m in height with open steel stairs outside the building which is not reaching to the roof where mechanical equipment are provided. However Ladder is provided to access this roof.
Note: building is fully sprinklered”
Building 3D snapshot is attached herewith for reference.
Is providing FHC for aforementioned flat roof in line with the NFPA requirements or suggest otherwise ?