Hello, i would like to ask about fire fighting and fire alarm inspection and maintenance visits, how many visits should be attended for a sea port facilities including a warehouses and marines as per NFPA?
Water based fire suppression systems must be inspected, tested and maintained according to NFPA 25, which has weekly, monthly, quarterly and annual frequency depending of type of system and its equipment.
NFPA 72 chapter 14 has ITM frequency requirements for fire alarm systems.
Other fire suppression systems have their ITM frequency requirements found in their respective NFPA standard.
Retrieving data ...