I've read through NFPA 30 looking for guidance on loading of liquid bulk containers inside of buildings. NFPA 30 chapter 28.4.1 states that loading facilities for Class I liquids (or Class II or III above flash point) need to be separated from above-ground tanks, warehouses, and other plant buildings by 25 feet . . . but doesn't seem to speak to whether or not the loading facility can be housed within a building.
With that, I'm looking for information on whether or not NFPA 30 (or other NFPA codes) allow for loading of Class I bulk containers inside of (or partially inside of) warehouse buildings. Any guidance in this regard would be appreciated.