Assembly occupancy, 8500sf, single story, NFPA 13 system, occupant load >300, water supply is water storage tank dedicated to sprinkler system.
NFPA 13 does not mandate the use of listed fire pumps, but they are an acceptable water supply source. However, if required to comply with NFPA 20 or even if required by an AHJ, then fire pumps must be listed.
Thank you for your response.
Jaome R. Blay
Santa Fe County Fire Marshal
Also, I believe NEC (NFPA-70) would require the fire pump to be listed, if it is an electric motor. 2017 NEC 695.10.
Retrieving data ...