I'm currently working on a project where I need to size the test header for a 1000 gpm pump. Do anyone have a calculation sheet to do so as per NFPA 20?
Please check NFPA-20 Table 4.26(a) Summary of Centrifugal Fire Pump Data for test test header sizes.
Thanks Jamsheer. But do I have to test the pump at 150% of its rated capacity? Is the above will be sufficient to do so?
You are testing @150%rated capacity as per NFPA recommendation,so this sizes from NFPA table shall be capable for the test.
Retrieving data ...