NFPA 130:2014 protection for battery and UPS Room
Dear Sirs. in my understanding of the NFPA:130: 2014, you shall to protect against fire (clean agent gas) the critical system for Metro, for example; signaling, power supply, telecommunication, but it is necessary to protect the UPS and battery room? if they are installed in different room that telecommunication and signaling?,
Please someone has a reference to the safety parameter for these room in NFPA 130?