In testing the inverter, when the utility input is off, simulating a power outage and exterior lights come on, it quits. All lighting is LED and by all indications the inrush is the problem. The lighting is 277V and I looked for a commercial add-on to limit inrush and did not find anything. The 1750W inverter is about 60% loaded. Anyone else had this problem and found a fix?