NFPA 13-2019 version clause 22.214.171.124. Fire pump room design density shall be 10.2 mm/min.
In a G+4 building fire pump room is located at basement. At fourth floor the furthest sprinkler design density is 6.1 l/min.
Question: In this case the hydraulic calculation of sprinkler shall be considered based on highest hazard i.e 10.2 mm/min from fire pump room or furthest sprinkler design density i.e 6.1 l/min at fourth floor?
Thanks in advance.