We are building apartments in Nevada. Does the fire alarm installer have the authority to install a wire with more conductors than the plan indicate? In our case, the plans show 18-2 for smoke detectors. Are we able to run 18-4 instead?
Not if the approved plans show something different. It seems like it would be a very simple plan revision to get, though.
Retrieving data ...