I have a 4000A, 480V main service with 1200A feeder breakers. These breakers have energy reduction mode and I can run the analysis with and without this. For example, at a board, with the reduction switch turned ON, it is 4.2 Cal and Level 3, with the switch OFF, it is 5.1 Cal and still level 3. For AF stickers, do you provide one with ON and one with OFF? As transformers are not listed in 110, should transformers such as a 75kVA get a label or considered non-serviceable?