what exactly does electrical continuity mean in a bonding or grounding sense per NEC.
i have 30" of 4" LFMC on one end of my pipe run that connects to 60 feet of 4" rigid
One end terminates in a switchgear and the other terminates in a generator enclosure
the voltage is 4160 and over 60 amps and there is a ground wire in the raceway Does this meet the requirement of 300.10 and 250.96 Electrical continuity LFMC is limited per 250.118(6)
Does electrical continuity mean that each end of the pipe is electrically connected to enclosure or does this mean that as long as the pipe has one path to ground that the
pipe is electrically connected?