With a meter main disconnect combo. Using the main lugs from the disconnect (not one of the additional breakers in the M M combo) to run cable to a interior panel board. Would this designate my Interior panel board as a sub panel? I would think not because the disconnect is not a breaker so this would be the same as a Installation direct from the meter? I would appreciate any ones opinion on this or direction to NEC code to reference.
Thanks in advance