Dear All ,
According to NFPA 2001, Ed. 2018, section 18.104.22.168:
22.214.171.124 Welding shall be performed in accordance with
Section IX, “Qualification Standard for Welding and Brazing
Procedures, Welders, Brazers and Welding and Brazing Operators,”
of the ASME Boiler and Pressure Vessel Code.
Please advise for this mentioned below application if X-Ray test for welded connections in the piping network is required or not: HFC227ea Fire Extinguishing System Piping :
- Type of pipes : carbon steel pipes to ASTM A106 gradeB
- Pipe schedule : SCH 80 for cylinder manifold only and SCH 40 for the other pipe work
- pipe sizes and wall thickness for the existing pipework :
3" pipe with wall thickness 5.5 mm
3" pipe with wall thickness 7.6 mm
4" pipe with wall thickness 6.0 mm
4" pipe with wall thickness 8.6 mm
We are unable to get this information from ASME standard mentioned above and your kind assistance.
3 Road 79 Apt. 101 Maadi, Cairo, Egypt.
Mob: (0020100) 5299466
Tel: 23809715 – 23592428