I'm installing a interactive solar photovoltaic sysyem
53.460 kWpdc Winston-Salem North Carolina
Fire Plan reviewer is requiring a center-line axis in both axes of the roof. 605.11.1.3.2 (2) I fully understand this design. However in California they have adopted some lead way.
605.11.1.3.3 (1) states 150x150 in distance in either axis in order to create opportunities for fire department smoke ventilation. I understand this refers to smoke ventilation but 150x150 in distance in either axis. 605.11.1 through 605.11.2 international building code. 605.11.1 Access pathways (2).
What information does anyone have to not change the design??