According to NFPA 110 2016 edition & NFPA 99 2018 edition. Level 1 building.
I have an electrical room, indoor, 2hr FR separation from the rest of building. Normal service entrance more than 1000 amperes and 150 volts to ground rated.
EPS outdoor located, in a housing.
Can the rest of EPSS equipment (over currents devices, transfer switches, cables, etc.) Be located in the same room with de normal service equipment?
Or shall be in a separate room?