Which edition of NFPA 58 are you referencing
Plus check the section
I want to say no, unless you design a room for over the MAQ. or, add a fire wall to make two buildings
But check the footnotes on how to increase 100 per cent
I am confused. I could not find Table 6.2.1 in the most current editions of NFPA 58. NFPA 58 has no provisions for control area only maximum storage quantities in various occupancies in a building. Refer to chapter 8 and 10 of the standard for storage of LPG.
Retrieving data ...