Hello NFPA Xchange, I have a question about the sprinkler system in high storage. Does any of you have experience with rack storage of 130,000 sq feet in the base and 100 ft height? I can not find in NFPA 13 standard how should storages of the height of about 100ft be protected? Racks are dimensions of 5ft 5inches x 5ft 5 inches in the base and the same 5ft 5inches height.
Thanks in advance!