Can pvc coated Mc cable be used under pavers on a terrace In nyc
According to the National Electric Code Article 330 330.12 , MC cable is permitted for direct burial when cable is listed for such use. You would need to confirm with the cable manufacturer it is listed for direct burial.
2020 NEC 330.10 (1-12). Type MC - Uses permitted
Manufacturer must specify it for use as direct burial.
2020 NEC 300.5 for min cover requirements of wiring method
The MC jacket would have to indicate "direct burial."
I believe it has to be IDENTIFIED for direct burial and that means have the marking.
It's probably listed, but not all listed cables are marked for direct burial.
Retrieving data ...